By Rob Clemons, Sales Manager, PCE Pacific, Inc.
Hi. I’m Rob Clemons, Sales Manager for the Instrument and Automation Division of PCE Pacific, Inc. I’ve got a great customer story to share with you. Chances are, most of you don’t own cruise lines, but as you can imagine, cruise lines have very stringent water quality rules – both for potable water and for water used in recreational facilities like hot tubs. The Center for Disease Control (CDC) places strict regulations requiring the continuous measurement of both halogens, such as chlorine, and pH. So we’re very honored to have been selected by the unique cruise line, Un-Cruise Adventures, as their water quality measurement company. This selection might have implications for your application as well.
The analyzer that proved to be ideal for the Un-Cruise Adventures application is the 56 Advanced Dual Input Analyzer configured for FCL (free chlorine) measurement. The 56 is a benchmark in ease of use and met the stringent requirements of the CDC.
The CDC regulations regarding measurement of halogens states:
A HALOGEN analyzer-chart recorder must be installed at a distant point in the POTABLE WATER distribution system where a significant water flow exists and represents the entire distribution system. In cases where multiple distribution loops exist and no pipes connect the loops, there must be an analyzer and chart recorder for each loop. Potable Water; 48 18.104.22.168.2 Data Logger Electronic data loggers with certified data security features may be used in lieu of chart recorders.
Needless to say, the choice of an electronic data logger is far superior in terms of precision, ease-of-use, and reduction in maintenance time. The CDC specifications go on to say:
22.214.171.124 Operation 126.96.36.199.1 Maintenance. A manual comparison test must be conducted daily to verify calibration. Calibration must be made whenever the manual test value is > 0.2 ppm higher or lower than the analyzer reading. 188.8.131.52.2 Calibration (06) The daily manual comparison test or calibration must be recorded either on the recorder chart or in a log. 184.108.40.206.3 Accuracy (05) The free residual HALOGEN measured by the HALOGEN analyzer must be ± 0.2 MG/L (ppm) of the free residual HALOGEN measured by the manual test.
The built-in data logger of the 56 again saves time, and enhances accuracy.
Un-Cruise Adventures is using the 56 equipment to provide CDC-mandated chlorine and pH control of three public hot tubs as well as for ensuring CDC compliance with onboard potable water systems on two passenger vessels. Since pH measurement is part of the free chlorine measurement on the 56, the system saved both time and money. To accommodate Un-Cruise Adventure’s space requirement, the back-panel of the assembly was trimmed down on one side and the 56 analyzer re-installed in order to fit inside a weather-proof enclosure they supplied. Our team is available to customize a system for you. Are there any water quality monitoring issues you have?
Dan Emigh, Port Engineer of Un-Cruise Adventures, stated, “I chose to use the Rosemount analytical equipment from Emerson for this important function based on my past experiences when installing this panel on our first vessel back in 2000. I had fantastic support from the rep and the equipment worked precisely as expected. When it became necessary to add the same type of equipment to the second vessel in 2014 I started by contacting Emerson and again received immediate and full support from the technical staff. As a direct result of the fantastic customer and technical service I have always received from everyone, I have no reason to consider anyone else for our water treatment needs. One phone call to Emerson and questions are answered, issues are resolved, and parts are on their way to our distant ships. Thanks for all the past and present support.”
And we didn’t even have to twist Dan’s arm to say that. Remember, the next time you’re sailing with Un-Cruise Adventures, the quality of the onboard water is in good hands.