By BonYook Koo, Sales Manager, Power and Steel & Iron
Today, I’d like to tell you how a South Korean power company has been able to maximize the efficiency of its furnaces and reduce furnace problems through the use of flue gas analysis. A South Korean power company has 8 boiler units, with #7 and #8 being 550MW units which employ tangential corner firing. See Fig. 1 and 2. In their units, the company has experienced heavy slag build-up in areas of the furnace where sufficient O2 was not provided to the flue gases, while in other areas where excess O2 values were experienced, damage from overheating often occurred.
This South Korean power company looked to Emerson for a Rosemount Analytical flue gas analysis solution. Combustion flue gas analysis has been used by process heater operators for decades as a method of optimizing fuel/air ratio. By measuring the amount of excess oxygen and/or CO in the flue gases resulting from combustion, furnace operators can operate at optimum efficiency and lowest NOx, and also generate the least amount of greenhouse gas. Today’s flue gas analyzers make this optimization process far easier and more precise due to different analyzer technologies and probe insertion lengths which allow different insertion configurations and approaches.
The readings from all 12 of these probes are averaged inside the customer’s Distributed Control System (DCS), and the primary air is controlled dynamically to a setpoint previously determined to be the optimum. The DCS bar graph readings from these units are shown in Fig 4. The plant engineers are not provided readings from each individual sensor since the variation in O2 can be misleading, however, the engineers have come to trust the probe readings. They understand that significant stratification in flue gases occurs as the gases pass through the ductwork. Based on the readings, they are able to make adjustments to individual burners in order to balance out the furnace as much as possible to minimize damage to the inside of the furnace.
This South Korean power company installation can be considered an example of “best practices” in applying flue gas analysis to optimize efficiency, while at the same time balancing the combustion within a large furnace in order to minimize slagging and tube damage from overheating. For additional pointers on the use of flue gas analysis, check out this Application Data Sheet.
We’d like to tempt you with a trip to Stuttgart! You’re aware of the dynamic interaction of Emerson Exchange, and that this 2014 event for Europe, the Middle East and Africa will be held April 1-3, 2014 in Stuttgart, Germany, right? were you aware that the event features more than 130 presentations, mostly from users, on real life case histories from 25 countries and a wide range of industries. You’ll find many things of significance to you at Emerson Exchange, and if you register before March 7th, you save up to 200 Euro off the fee. (Of course, if you’re not lucky enough to go to this event, you can share in many of the findings through Emerson Exchange 365).
The 2014 Conference Presentation Tracks include: Operate Safely & Legally, Maintenance, Reliability & Asset Optimisation, Energy Management, Process Optimisation, Business Management & Information Security, Instrumentation Applications, Valve Applications, Wireless Applications, Project Excellence and Control System Applications & Migrations. The in-depth Industry Forums cover Chemical, Engineering, Life Sciences, Oil & Gas, Power, Refining and Petrochemical, while the “Meet the Experts” sessions give you the chance to ask questions specific to your operations and challenges. There’s even a networking event at the Porsche Museum.
When you attend, watch for these exciting sessions from Rosemount Analytical –
Reganosa has used the available equipment for a standard LNG import terminal and with the support of Emerson adapted it for export activity, turning it into a unique tool to achieve our clients’ satisfaction.